Thank you to everyone who participated, and congratulations to our winner Michael Cerchia!
Rogue Receptacle Installation
Brandon Spivey, owner of Event Horizon & Services in Nashville, Tenn., was kind enough to share this photo with us. He said, “The plugs were covered with a fabric panel with no other housing.” Brandon also said he is “new to this all, and learning, but this seems like a Code violation.” Brandon, you are correct. There are definitely Code violations here. Section 406.5 requires receptacles to be mounted in identified boxes or assemblies. Attaching receptacles to a couple of wooden blocks does not meet Code minimum requirements. It appears these boards were being used as some type of “box extender.” A listed extension ring or listed box extender should have been secured to the flush-mounted box instead. The exposed energized terminals create a shock hazard and violate the rules of Sec. 406.5(I), which requires receptacles to be enclosed so that no live terminals are exposed to contact. The lack of a box cover for the outlet box is a violation of Sec. 314.25. We also accepted 406.6.